Navigate to the DHW/Boiler library and create a new Water Heater. Set the Water Heater Type to “Heat Pump”. Enter the Volume, Uniform Energy Factor and Input Rate from the manufacturer’s specifications. Note that sometimes the Uniform Energy Factor may be listed as the COP in the data.
For residential projects (single family, multi-family, high-rise residential, hotel/motel), you may select a model that has been tested by the Northwest Energy Efficiency Alliance (NEEA) by clicking on the green Import button on the library toolbar. Note that for NEEA rated models, the efficiency is not relevant since the NEEA selections contain performance curves specific to that model.
Note that you cannot use a Heat Pump Water Heater as the heating source for the home. In this circumstance, the CEC requires you to model this as Electric Heat. You cannot input the Heat Pump Water Heater as ANY source of hot water for either a Hydronic Heating System, nor for a Combined Hydronic Heating System. You will need to model this as electric heat.
As of EnergyPro v6, the energy budget for your building is set internally by the CEC supplied compliance engine (CBECC). As such, we do not have control or access to that feature so any questions on the energy budget should be directed to the CEC hotline at (800) 772-3300. The CEC publishes a document called the Alternative Calculation Method (ACM) manual, you can Google this and take a look at this document. Also, some of the training classes on the code will give you insight into that, and in the case of the Residential software, Package A in the Standards would be your starting point. For Nonresidential lighting and envelope, the Prescriptive section of the Standards would also be a good starting point, but the HVAC is detailed in the ACM manual. Look in the EnergyPro Help for some information on those tables also.
You can edit the specs on an existing system or assembly from the libraries in EnergyPro or you can use the “Add new” button to create your own.
1. The EnergyPro libraries come pre-populated with most of the common utility rates in California.
2. Select an electric/gas utility rate at the Building level of the Tree, Utility tab. Note when selecting one you can use the green Import button to pick from a list.
3. Go to Calculations and check the box for the particular calculations you wish to run.
5. In the Report Wizard, Select the report labeled “ECON-1”, and proceed to finish.
6. Click the Print Preview button.
Under Help | EnergyPro News, we have a news feed that will alert you automatically to any new updates published for the software.
To create hourly output files in a CSV format (readable by Excel), you need to go to the calculations button on the bottom left, and then select whichever calculation you are working on (NR Title 24 Performance, NR ASHRAE 90.1, etc.) in the list above. Deselect ‘Delete Temporary Files after Simulation is Complete’ and then select ‘Generate CSV Output File Containing Detailed Results’ as shown in the screenshot below. Now run the calculations and the CSV file will be found in the Results folder located under My Documents/ EnergyPro 7/ Results. See screenshot below.
The best way to create your own utility rate is to edit one of the utility rates that are already in the list. You will have to get the information from the utility company on their actual costs.
At the top level of the Building Tree, start by selecting a location that is in the correct Climate Zone from the selections listed. This ensures that your report will use the correct code requirements for compliance. You can then check the box for “User Defined” location and modify the design conditions based upon data that you may have, ensuring that your load calculations are done with the correct data.
Click on the red “X” to the left of the entry. Select Yes when asked to confirm the deletion. Your input will show Undefined. (Note: this operation will not delete the item from the library.)
EnergyPro contains the complete list of CEC certified equipment directories. To select an item from this list, click the new option at the Central System Library editor. Once you are in the edit menu for the system, select the green import button at the top of the dialog. By clicking this button EnergyPro will allow you to select a system from the CEC equipment listings and add it to your working library.
When a new window is created in EnergyPro it is created specific to your file, meaning that the item will only appear in the file being modified. Once inside the Fenestration Library select the window that you have customized and click on the Export button. The program will ask you to select a destination, by selecting the Default Library and mouse clicking the OK option, the window you have created will now be added to the Default Library. Any new projects that you start will automatically include the contents of the Default Library. However, the window you just created will not appear in an other projects that have already been created.
This window can be exported to an older project by exporting from the default library to the older project file. The default libraries can be accessed under Tools | Default Libraries.
You will have to input an interior window as an interior door in an interior surface (wall).
A user may combine systems or any input for that matter that are identical and whose requirements do not mandate that detailed inputs be used. When combining inputs, be sure to keep track of the multipliers and that your floor levels are being reported correctly. The criteria in this case would be that the systems serve zones that are thermally identical. An example of this would be a core zone of a building. Five different orientations would not meet this criteria. Consult the CEC’s Residential and Nonresidential Manual for information on the depth of detailed information that may be required for the situation in question.
EnergyPro requires that you input your heat pump heating capacity at the AHRI rating condition of 47 degrees F dry-bulb. Typically, design conditions at your actual site are much colder, so EnergyPro will de-rate the heat pump capacity, based upon this condition.
EnergyPro requires that you input your air conditioner cooling capacity at the AHRI rating condition of 95 degrees F dry-bulb outside air, 67 degrees F wet-bulb entering air. Typically, design conditions for your building will be different. Changes in outside design conditions and indoor entering air conditions will result in a different overall capacity for your system than the value you specified in the library.
The latest version of EnergyPro can read any of the older version 6 or version 7 files.